V.C Summer Unit 1 has encountered restricted flow on the Floor Drain Tank
filter while attempting to transfer the Floor Drain Tank water to the Waste
Monitor Tanks (release tanks). The flow restriction was observed at the
beginning of the transfer - within 30 minutes of start or at about 500 gallons.
The filter we currently use
is 30 micron and is 3 inches in diameter by 11.5 inches long.
We would like to know if you have experienced any problems with your FDT
filter. If so, what was the problem and your solution?
Please provide the following:
Type of filter:
Please respond directly to Ryan Fogle at
rfog...@scana.com<mailto:rfog...@scana.com> or 803-345-4217