What is the structure of the freezer? Are the racks integral to that structure,
or free standing? Could you support system from racks?
Sent from my iPhone
> On Sep 18, 2016, at 10:13, rongreenman . <rongreen...@gmail.com> wrote:
> For once we have s post where a double interlock pre action is actually the
> proper system and our fellow forumite wants to use a single interlock. If you
> use a SIPA you'll have ice in your pipes before a head fuses. A DIPA WONT
> FLIW Wter into the piping until sprinklers are fused.
> On Sunday, September 18, 2016, 321 <tcf...@bellsouth.net> wrote:e
>> I have a very large Freezer/Cooler project that I am managing. My initial
>> idea on this job has been to use a Wet Pipe System above the Freezer with
>> ESFR Dry Pendents (Class IV in rack to 20'). Due to the exorbitant cost of
>> the ESFR Dry Pendents I'm letting my thinking expand to possibly running
>> Single Interlock Pre Action inside the Freezer ...since the Freezers are
>> already up (yeah...I know !!).
>> The ceiling panels are 6" thick and I was wondering if any of you guys in
>> your history have ever hung Fire Sprinkler Pipe inside a Freezer attaching
>> to/thru the panels and how?
>> Thanks in advance
>> Atlantic Realty and Building, LLC
>> Palm Beach Gardens, Fl
>> John W. Farabee
>> V.P. Fire Sprinkler Division
> Sent from Gmail Mobile
> Sprinklerforum mailing list
Sprinklerforum mailing list