Not an overhang. The entry way juts into the warehouse so that the roof of the
building is still overhead fully protected and there is a 20ft gap then the
entry way. Since its cold in the winter here I would need to install a dry
pendant to protect the space below the entry ceiling. Just trying to avoid this
Sent from my iPhone
> On Oct 18, 2016, at 5:02 PM, Brad Casterline <bcasterli...@gmail.com> wrote:
> Sounds like an exterior floor space with no fuel load to me. The 10 ft high
> noncomb ceiling is an overhang?
> I'm gonna scratch my head on 22.214.171.124 a while, but I don't think that's your
> get out of Sprink free card here.
>> On Oct 18, 2016 7:38 AM, "Dewayne Martinez" <dmarti...@total-mechanical.com>
>> NFPA 13 (07ed)126.96.36.199
>> I have a warehouse that is 30ft tall with inset entryways with
>> non-combustible walls/doors on 3 sides and open on the 4 to the outside. The
>> entryway is about 10ft tall with a noncombustible ceiling. Would 188.8.131.52
>> (or any other rule) allow me to omit sprinkler protection for this? No
>> combustibles will be stored below.
>> Sprinklerforum mailing list
> Sprinklerforum mailing list
Sprinklerforum mailing list