The industry has used spray sprinklers with glazing as an alternate approach for a long time. Having said that, the ONLY place it is official blessed is for Atrium glass (unless something was added since I looked a couple of cycles ago but with the WS sprinkler covering a wider spectrum not a lot of energy being invested on said other places). Since 13 says use a listed sprinkler or allowed by the codes, that narrows the easy application to that described by the mfg cut sheet or for atrium glass.
Regarding the NFPA 101 guidance, I’ve always been worried (in our crazy world of litigation) about proving the requirement to wet the ENTIRE surface with a parabolic pendent sprinkler (which gets little or no attention in the evaluation). Just because an AHJ accepts it doesn’t mean one of my fellow Prostitutes Extraordinaire won’t help some dirt ball attorney sue you. SO the first question is, is it worth the effort. Roland Roland Huggins, PE - Senior VP Engineering American Fire Sprinkler Assn. Dallas, TX http://www.firesprinkler.org <http://www.firesprinkler.org/> Fire Sprinklers Saves Lives > On Feb 13, 2018, at 2:57 PM, Jerry Van Kolken <jvankol...@mfpc.us> wrote: > > Okay, Is been about a decade since I’ve dealt glazing protection. Is there > any information on protecting window with standard spray sprinklers. I’ve > been told this was direction was approved by the AHJ. > > Jerry Van Kolken > Millennium Fire Protection > (760) 722-2722 > _______________________________________________ > Sprinklerforum mailing list > Sprinklerforum@lists.firesprinkler.org > <mailto:Sprinklerforum@lists.firesprinkler.org> > http://lists.firesprinkler.org/listinfo.cgi/sprinklerforum-firesprinkler.org > <http://lists.firesprinkler.org/listinfo.cgi/sprinklerforum-firesprinkler.org>
_______________________________________________ Sprinklerforum mailing list Sprinklerforum@lists.firesprinkler.org http://lists.firesprinkler.org/listinfo.cgi/sprinklerforum-firesprinkler.org